Industrial Smart.Hubs™ include a Modbus TCP client that can be used to create a 2 way connection between any Modbus TCP enabled device and the Whisker.io® web portal, allowing users to remotely monitor and manage automation technologies from anywhere in the world.
Modbus is the most popular and well-supported communication protocol for industrial automation applications. It is used for:
- Programmable Logic Controllers (PLC)
- Human Machine Interfaces (HMI)
- Variable Frequency Drives (VFD)
- Remote I/O
- Building Automation
- and more...
Smart.Hub™ IoT gateways include a Modbus Client that allows a two-way connection between any of these devices and our cloud platform.
Once the Modbus Client is configured, the Smart.Hub immediate begins to read data from the configured devices and report it to the cloud, where it can be used in HMI user-interfaces, dashboards, and the alerting system.
Smart.Hub Modbus Client Operation
The Smart.Hub Modbus Client communicates with one or more Modbus devices to collect data on assets and equipment in the field.
The Smart.Hub Modbus Client is configured using the concept of slots. A slot definition contains all of the information needed to collect a reading from a Modbus enabled device and display it in the cloud using NexusHMI.
Slot configuration is separated into two parts: Modbus and Scaling & Units.
Modbus configuration parameters include everything needed to access a value in a Modbus enabled device. Each slot can be configured to read from a different device, table, and register.
Slot Modbus Parameters
|IP Address||TCP/IP Address of device on the network|
|Port||Modbus Port (usually 502)|
|Table||Table (Coils,Discrete In,Input Regs, Holding Regs)|
|Data Type||Size and format of the data. 16/32 bit words, bitfields, and floating point are supported.|
|Start Address||The starting address of the register containing the desired value|
|Writable||Set to true if the value is writable. This allows the value to be changed in the cloud.|
Scaling & Units parameters are used by the cloud to properly scale and display the values read from Modbus devices. The parameters vary with the data type.
Slot Scaling & Units Parameters (Float and Word types)
|Name||This is used to identify a value when displayed|
|Gain||Used to scale the incoming value. The displayed value is the measured value multiplied by the gain and then added to the offset (standard slope formula).|
|Gauge Min||Determines the minimum range of a gauge when used to display a value|
|Gauge Max||Determines the maximum range of a gauge when used to display a value|
|Units||Set to a string representing the units of the scaled value|
|Decimal Places||Number of decimal places to displaying a value|
The Modbus and Scaling & Units parameters are grouped together into a slot to save time during configuration.
When Modbus slot configuration is changed in the cloud, the changes are immediately pushed to the Smart.Hub and, within a few seconds, the Smart.Hub will begin gathering values and reporting them to the cloud.
Data Types for Modbus Slots
|Data Type||Description||Coils||Discrete In||Input Regs||Holding Regs|
|Bitfield16||16 bits packed into a word. Treated as individual channels/tags in Whisker.io® portal.|
|Word32||32-bit word constructed from two 16-bit registers|
|Word32S||Same as Word32, but with the 16-bit words swapped|
|Float||32-bit floating point|
|FloatSB||Float with bytes swapped in each word|
|FloatSW||Float with words swapped|
|FloatSBW||Float with bytes and words swapped|
|Multiselect||16-bit word used to select mode/status. Each unique values represents a status or mode|
Configuring Smart.Hub Modbus Client
Every Industrial Smart Hub includes a Modbus Client, but it must be enabled and configured. It is important to note that enabling a Modbus Client will add monthly or annual charges to your account (see Subscription Agreement and Offer Details).
The Smart.Hub Modbus Client is configured using the Whisker.io® web portal. To get started, log into www.whisker.io and navigate to the Location View for the location that contains the Smart.Hub you wish to configure.
Now, click the "gear" icon on the right side of the Smart.Hub's name in the Configured Products panel:
This will open the "Edit Gateway" dialog:
|1||Smart.Hub name. This is used to identify the Hub in the cloud.|
|2||Check to enable Modbus Client. This will incur additional charges if this service is not already included in your Offer Details.|
|3||Timeout in seconds for write commands. Applies to Writable slots.|
|4||Click to edit ethernet configuration parameters.|
|5||Click to edit Modbus Client slots|
For the Modbus Client to work properly, you must ensure that the Ethernet settings are correct for your network.
The IP address is the fixed address of the Smart.Hub on your network. This is in CIDR notation with the subnet being specified by a single number. If you are not familiar with CIDR notation, this chart is a good cheat sheet for making the conversion. Ensure that the ethernet IP address and subnet are configured properly or the Smart.Hub will not be able to communicate with your Modbus TCP devices.
The Smart.Hub must have access to the Whisker.io® MQTT and cloud servers which requires DNS service to be available. Ensure that at least one name server and the gateway IP are configured properly or the Smart.Hub will not be able to reach the servers on the Internet. This is important even if you are using 4G cellular as your primary Internet connection because the Ethernet channel is used as backup if cellular is lost temporarily.
With the Ethernet interface configured properly, you can now configure the Modbus Client slots. Click the "Modbus Client" tab to view the available slots:
The Modbus Client has 32 slots which are displayed here in a scrollable list. If a slot is not configured, it will be marked "Inactive". The Smart.Hub will ignore inactive slots.
To activate or edit a slot, click the "gear" icon for that slot to bring up the "Edit Slot" dialog:
This slot is not active. To activate and configure the slot, check "Slot Active":
To add/edit alerts (alarms) for this slot, click the "View Alerts" button.
These parameters where explained earlier in this article. Please refer to the tables labeled "Slot Scaling & Units Parameters" and "Slot Modbus Parameters" for more information.
"Slot Type" is the datatype for this slot. It is used by the Modbus Client to know how many words to read and how to organize the bytes, and by the Whisker.io® web portal to determine how Scaling & Units should be configured to properly display the value.
The "Scaling & Units" parameter editor will change based on the value type. For 16/32 bit words and floating point numbers, the editor will look as shown in the picture above. This provides you with the ability to scale the incoming analog value.
If the type is "Multiselect", the editor will change to allow you to specify the selection parameters. This is useful when you want to use a word to encode various states. For example, you would use multiselect for a word that sets the A-H-O (Augo-Hand-Off) operating mode:
If the type is "Bitfield16", the edit will change to allow you to specify the parameters for each bit in a 16-bit word. This datatype can be used with Coils, Discrete Inputs, and Holding Registers.
When a slot is configured for Coils or Discrete Inputs, the datatype must be Bitfield16 and the Modbus Client will read 16 continuous bits starting with the Start Address for the specified device.
When a slot is configured for Holding Registers and the datatype is Bitfield16, the Modbus Client treats it as a 16-bit word but the Whisker.io® portal treats it as individual bits, allowing you to pack status bits into a single register.
Since each bit is treated as a separate tag in the Whisker.io®, alerts are configured on a bit-by-bit basis. Click the "View" button to add/edit alerts for a bit in the bitfield.
Once you have finished configuring a slot, click "Close" to return to the "Edit Gateway" dialog.
When all slots are configured the way you want them, click "Save Changes" to store the new configuration and send it to the Smart.Hub. Within a few seconds, the Smart.Hub will begin acquiring values based on the new configuration and reporting those values to the cloud.
Generally, Smart.Hubs are configured to update the cloud once every minute, so it might take a minute before you start to see the values change in the cloud.
Each word and float type slot is treated as a channel (tag). Each bit in a bitfield is also treated as a channel (tag). You can view the Smart.Hub's channels in the Configured Devices panel in the Location View.
The channels can now be used for Alerts, NexusHMI, and Dashboards.